The Gamewell-FCI Power Supply 6 (GFPS-6) panel provides two (2) Class A, Style Z, or four (4) Class B, Style Y notification appliance circuits.
Each circuit is rated at 3 amperes, with a total capacity of 9 amperes per panel. These circuits may be programmed to activate by groups or various combinations by connection to one (1) or two (2) existing Class A or B notification appliance circuits with operating voltages ranging from 9 to 30 VDC. Either non-coded or coded operation is possible. In addition, the GFPS-6 can provide a temporal pattern output from a non-code
- The GFPS-9 contains its own battery charger capable of maintaining batteries of up to 35 AH. The cabinet provides space for a set of 7 A/H batteries. It is supervised for ground fault, over-current, open circuits and low battery conditions. These conditions light the appropriate trouble LED and automatically open the notification appliance circuit used for activation, transmitting a trouble signal to the main fire alarm control panel. The ground fault detection circuit may be disabled. Note: Larger batteries require a separate battery box. The unit contains a set of dry, Form “C” trouble actuated auxiliary contacts, rated 2.5 amp. @ 24 VDC (resistive). Transfer of these contacts for AC power failure is programmable and can be delayed for a period of six (6) hours. This delay feature may be disabled.
|Operating Power:||120 VAC, 3.6 amp. 60 Hz
Wire Size: minimum #14 AWG (2.0mm2) with 600 V insulation
|Standby Battery Circuit:||24 VDC (nominal) 7 ampere/ hours, max.|
|Supervisory Current: Alarm Current:||0.075 amp.0.175 amp. (excluding notification appliances)|
|Alarm Output:||(excluding notification appliances) 6.0 amp. max. @ 24 VDC (nominal)|
|Dimensions:||16" H x 12.25" W x 3" D (40.64 x 30.88 x 7.62 cm)|
|Operating Temperature:||32° to 120° F (0° to 49° C) Relative Humidity: 10 to 85% @ 86° F (non-condensing)|