FCPS24FS8B BOARD ONLY is a compact, cost-effective, 8-amp remote power supplies with battery charger. The FCPS24FS8C/E) may be connected to any 12 or 24 volt fire alarm control panel (FACP) or may stand-alone. Primary applications include notification appliance (bell) circuit (NAC) expansion (to support ADA requirements and NAC synchronization) or auxiliary power to support 24 volt system accessories.The FCPS provides regulated and filtered 24 VDC power to four notification appliance circuits configured as either two Class B (Style Y) and Class A (Style Z, with ZNAC-4 option module) or four class B only. Alternately, the four outputs may be configured as any combination of resettable/non-resettable power outputs (optimal for powering four-wire smoke detectors. The FFCPS24FS8(C/E) also contains a battery charger capable of charging up to 18.0 Amp hour batteries. FCPS24FS8C/E) is ULC-listed.
• UL-Listed Notification Appliance Circuit (NAC) synchronization using System Sensor, Wheelock, or Gentex “Commander2”appliances.
• Operates as a “sync-follower” or as a “sync-generator” (default). See note on page 2.
• Contains two fully-isolated input/control circuits – triggered from FACP NAC (NAC expander mode)or jumped permanently “ON”(stand alone mode).
• Two Class B (Style Y) or Class A (Style Z, with ZNAC-4 module) NACs (circuits 1 & 3)
• 8-amp full load output, with 3 amps maximum/circuit, in NAC expander mode (UL 864).
• 6-amp continuous output in stand-alone mode (UL 1481).
• Compatible with coded inputs; signals passed through.
• Optional power-supervision relay (EOLR-1).
• In stand-alone mode, output power circuits may be configured as: resettable, (reset line from FACP required),non-resettable, or a mix of two and two.
• Fully regulated and filtered power output - optimal for powering four-wire smoke detectors, annunciators, and other
system peripherals requiring regulated/filtered power.
• Power-limiting technology meets UL power-limiting requirements.
• Form-C normally-closed trouble relay.
• Fully supervised power supply, battery, and NACs.
• Selectable earth fault detection.
• AC trouble report selectable for immediate 2-hour delay.
• Works with virtually any UL 864 fire alarm control which utilizes an industry-standard reverse-polarity notification circuit
(including unfiltered and unregulated bell power).
• Requires input trigger voltage of 9 - 32 VDC.
|Primary (AC) Power||FCPS-24FS8: 120 VAC, 60 Hz, 3.2A maximum
Wire Size: minimum #14 AWG (2.0mm2) with 600 V insulation
|Trigger Input Voltage||9 to 32 VDC|
|Trigger Current||2.0 mA (16 - 32 V); Per Input: 1.0 mA (9 - 16 V)|
|Trouble Contact Rating||5 A at 24 VDC|
|Auxiliary Power Output||Specific application power 500 mA maximum|
|Output Circuits||+24 VDC filtered, regulated
3.0 A maximum for any one circuit
Total continuous current for all outputs (stand-alone mode):
FCPS-24FS8: 6.0 A maximum.
Total short-term current for all outputs (NAC expander mode):
FCPS-24FS8: 8.0 A maximum.
|Secondary Power (Battery) Charging Circuit||Supports lead-acid batteries only
Float-charge voltage: 27.6 VDC
Maximum current charge: 250 mA
Maximum battery capacity: 7.0 AH.